|Name:||JAPAN ORION Heatless Dryer QSQ Series||Working Pressure:||6-10bar|
|Packing Box:||Export Plywood Box|
10 bar Regenerative Air Dryer,
1.5nm3 Min Regenerative Air Dryer,
6 bar Adsorption Compressed Air Dryer
High Pressure Heatless Regenerative Adsorption Compressed Air Dryer Air Cooling 1.5nm3/Min
AETOK is an agent of ORION machinery (Shanghai) Co., LTD., a foreign enterprise established by ORION co., LTD., which is specialized in producing oil-free vacuum pumps and air compressor post-treatment equipment in China. Main business scope: production and sales of vacuum pumps, industrial compressed air dryers, water coolers, industrial jet fuel heaters, hePA filters, dairy machinery and other related parts and components.
|Pressure Dew Point||-20~-40℃|
|Regeneration Gas Consumption||≤13%|
|Inlet oil content||≤0.1ppm|
|Control Mode||Microcomputer Automatic Control|
Energy-saving dew point sensor with standard configuration (medium and large series)
All function indicators are displayed.
Small size, light weight, convenient maintenance.
Heatless Adsorption Dryer Workflow
|1.Two towers drying in parallel
Before start-up, the inlet and outlet valves of the left and right towers are always open, and compressed air passes through both towers to the point of use at the same time.
2. The left tower is dried and the right tower is regenerated
After the power is turned on, the right tower inlet / outlet valve is closed, the right tower regeneration inlet / exhaust valve is opened, and the compressed air flows through the left tower to be dried. The dry air passes through the orifice plate, and the right tower is regenerated after being throttled and expanded.At this time, the pressure of the right tower should be 0 kg. The compressed air containing moisture is released into the atmosphere through the right tower regeneration exhaust valve and muffler.
left and right towers are always open, and compressed air passes through the two towers to the point of use simultaneously.
|3.Regeneration is over, ready to boost
After 4 and a half minutes of regeneration, the right tower regeneration exhaust valve was closed, and the right tower began to boost pressure.
|4. The left tower is dry and the right tower is boosted
The booster valve opens, and the pressure of the two towers slowly rises to equilibrium.After 5 minutes, the tower is changed to enter the next cycle.
Contact Person: admin