|Lubrication Style:||Lubricated||Voltage:||380v/3ph/50hz(or Customized)|
|Packing Box:||Export Plywood Box||Rated Pressure:||0.6-1.0MPa|
0.7mpa regenerative dryer aetok,
aetok 50hz adsorption dryer compressed air,
aetok 0.7mpa regenerative dryer
Heat Regenerative Adsorption Type Compressed Air Dryer Adsorb Dryer
Modular adsorption dryer is a high value-added product newly developed by Lingyu company. Compared with the traditional dryer, this series of products are smaller and smaller. 13X molecular sieve and straight through adsorption chamber make the adsorbent more efficient. At the same time, the whole machine is mainly made of high-quality aluminum alloy, which avoids secondary pollution to the compressed air.
The adsorption module of the modular adsorption dryer is composed of a number of high-strength 6063-T5 aluminum alloy cylinders, each of which is divided into two cavities A and B, and the cavity is filled with adsorbent. When cavity a is adsorbed, cavity B is regenerated by means of decompression regeneration. When cavity B is working, cavity a is regenerated by means of decompression regeneration, and two cavities A and B work alternately.
|Product name||Modular adsorption dryer|
|Rated air inlet pressure||0.7MPa|
|Rated intake air temperature||10 ℃~ 30 ℃|
|Atmospheric dew point of finished gas||- 40 ℃|
|Ambient temperature||≤ 45 ℃|
|Pressure loss||≤ 0.02MPa|
|Adsorbent||high efficiency molecular sieve|
|Product Keywords||air dryer heatless,air dryer for compressor,air dryer compressed|
Main tech parameters:
Energy-saving dew point sensor with standard configuration (medium and large series)
All function indicators are displayed.
Small size, light weight, convenient maintenance.
Heatless Adsorption Dryer Workflow
|1.Two towers drying in parallel
Before start-up, the inlet and outlet valves of the left and right towers are always open, and compressed air passes through both towers to the point of use at the same time.
2. The left tower is dried and the right tower is regenerated
After the power is turned on, the right tower inlet / outlet valve is closed, the right tower regeneration inlet / exhaust valve is opened, and the compressed air flows through the left tower to be dried. The dry air passes through the orifice plate, and the right tower is regenerated after being throttled and expanded.At this time, the pressure of the right tower should be 0 kg. The compressed air containing moisture is released into the atmosphere through the right tower regeneration exhaust valve and muffler.
left and right towers are always open, and compressed air passes through the two towers to the point of use simultaneously.
|3.Regeneration is over, ready to boost
After 4 and a half minutes of regeneration, the right tower regeneration exhaust valve was closed, and the right tower began to boost pressure.
|4. The left tower is dry and the right tower is boosted
The booster valve opens, and the pressure of the two towers slowly rises to equilibrium.After 5 minutes, the tower is changed to enter the next cycle.
Contact Person: admin